On this project, Mercury was commissioned to carry out the internal fit out of 3 data halls, plus 1 fallow data hall and all associated mechanical and electrical infrastructure. The data halls were formed using white wall panels and are approximately 1300m2 each and have raised access floors and suspended ceilings. The data halls are cooled using chilled water CRAH units supplied from a shared group of adiabatic and water-cooled chillers. The suspended ceiling acts as a hot air return plenum.
The data halls have a shared common cooling plant and the chilled water is distributed via high level ring mains to the 48No CRAH units. The cooling plant comprised of water-cooled chillers located in packaged pump rooms, adiabatic and hybrid coolers.
The electrical infrastructure included 6No. HV standby generators with bulk fuel storage tanks, 3No HV Generator switch panels, 2No. HV switch panels, 8No. DYN11 Transformers, 8No. LV Panel and 20No. Static UPS’ which in turn supply the data hall PDU’s. The sprinkler system was designed, supplied and installed by our Fire Protection business unit and a water mist system was installed into the data halls.